Dear Emerson Support
We are using the following DVC6200 series positioner:
FW Rev = 6
We configured Lo Limit/Cutoff point in our DVC6200 positioners at 10%. Now the positioner is in service and we want to change it to 5%. But the Valvelink is not allowing us to do so. Is this feature only editable when the valve is out of service?
If it requires the valve to be out of service, then when we will change the valve mode to be out of service, will the valve hold its position or will move to some extreme position?
Is there any DVC6200 document which clearly informs which features can be edited online and which need valve to be out of service?
Thanks in advance.
This is the official online community site of the Emerson Global Users Exchange, a forum for the free exchange of non-proprietary information among the global user community of all Emerson Automation Solution's products and services. Our goal is to improve the efficiency and use of automation systems and solutions employed at members’ facilities by sharing our knowledge, experiences, and application information.
User Groups |
World Areas |
Community Guidelines |
Legal Information |
Contact Community Manager
Website translation provided by
© 2015-2020 Emerson Global Users Exchange. All rights reserved.