We are taking KWH reading from secure premier to DCS but value not matching.how to correct the same in SLCAIN block
I am not an expert on Modbus interfaces; however, some of the answers you are looking for may be located within the Ovation Users’ Group website. (https://www.ovationusers.com)
The Ovation Users’ Group website contains a “Third Party Connectivity” tool for selecting the appropriate interface to a third-party device, and it also hosts the Ovation user manual library – including user manuals for various data links including Modbus.
If you don’t have an account on the website, I recommend registering for one.
I hope this might help you a little bit.
This is the official online community site of the Emerson Global Users Exchange, a forum for the free exchange of non-proprietary information among the global user community of all Emerson Automation Solution's products and services. Our goal is to improve the efficiency and use of automation systems and solutions employed at members’ facilities by sharing our knowledge, experiences, and application information.
User Groups |
World Areas |
Community Guidelines |
Legal Information |
Contact Community Manager
Website translation provided by
© 2015-2020 Emerson Global Users Exchange. All rights reserved.