Please tell me how to get the feedback of a DVC6000 HART communicating, through the HART network I get this?
I could verify that the DVC6200 is an out for this feedback....
In reply to Nathan_McCormick:
In reply to Jonas Berge:
If connected with HART Passthrough system, HART command 3 will provide travel feedback
If it is old legacy system, than you can use TriLoop or HIM kind of devices to provide travel feedback.
If you are using DVC6200, than there is option to get AI (4-20mA) from DVC, which is completely independent of positioner signal.
In reply to Javier:
This is the official online community site of the Emerson Global Users Exchange, a forum for the free exchange of non-proprietary information among the global user community of all Emerson Automation Solution's products and services. Our goal is to improve the efficiency and use of automation systems and solutions employed at members’ facilities by sharing our knowledge, experiences, and application information.
User Groups |
World Areas |
Community Guidelines |
Legal Information |
Contact Community Manager
Website translation provided by
© 2015-2020 Emerson Global Users Exchange. All rights reserved.