We have discussed the use of Diagnostic Channels in this thread:
Siemens ET200S works fine as per KBA AUS1-131-000601153757.
Does anyone have experience with Festo CPX-4AE-U-I? Which channel to configure?
So we found that it does work to some extent, but it has an issue: only the first faulty channel is reported. So if we have 4 AI channels and the first and second are both faulty, only the first is reported as faulty. This is also documented in the manual.
This is the official online community site of the Emerson Global Users Exchange, a forum for the free exchange of non-proprietary information among the global user community of all Emerson Automation Solution's products and services. Our goal is to improve the efficiency and use of automation systems and solutions employed at members’ facilities by sharing our knowledge, experiences, and application information.
User Groups |
World Areas |
Community Guidelines |
Legal Information |
Contact Community Manager
Website translation provided by
© 2015-2020 Emerson Global Users Exchange. All rights reserved.