Wide-open monitors are the most common form of overpressure protection in large gas distribution applications such as city gate stations, district stations, and large industrial meter sets.
Wide-open monitor setups utilize a second regulator (called the monitor) in series with the worker regulator where both regulators sense downstream pressure. The monitor is set slightly above the worker pressure setting, keeping it open and in standby. If the worker malfunctions and outlet pressure rises, the monitor will take over control at its pressure setting.
The monitor can be either the upstream or downstream regulator. Also, both pilot-operated regulators and direct-operated regulators can be utilized in a monitor setup as long as the upstream regulator has external registration in order to sense the pressure after the downstream regulator.
Conditions after worker failure:
This is the official online community site of the Emerson Global Users Exchange, a forum for the free exchange of non-proprietary information among the global user community of all Emerson Automation Solution's products and services. Our goal is to improve the efficiency and use of automation systems and solutions employed at members’ facilities by sharing our knowledge, experiences, and application information.
User Groups |
World Areas |
Community Guidelines |
Legal Information |
Contact Community Manager
Website translation provided by
© 2015-2019 Emerson Global Users Exchange. All rights reserved.