I use CPL410 (Firmware 10.15) as primary and secondary PLC. I use Lan 2 in both CPL410 as Profinet and Lan 3 use to be redundancy link. Both of CPL wiring by MRP ring.
Redundant is OK.
Primary Profinet Explorer.
Secondary Profinet Explorer.
Right is Primary and Left is Secondary PLC. Light in IO Secondary not On.
In front panel primary IO status "ALL Device Connected"
In front panel secondary IO status "No Device Connected"
Question : Why light bulb IO secondary not on ?
This is the official online community site of the Emerson Global Users Exchange, a forum for the free exchange of non-proprietary information among the global user community of all Emerson Automation Solution's products and services. Our goal is to improve the efficiency and use of automation systems and solutions employed at members’ facilities by sharing our knowledge, experiences, and application information.
User Groups |
World Areas |
Community Guidelines |
Legal Information |
Contact Community Manager
Website translation provided by
© 2015-2022 Emerson Global Users Exchange. All rights reserved.