We have positioner as below.
Before replacement, our DCS is configured 4mA to full open, 20 mA to full close with DVC6010. After we replace with new DVC6200 SIS Relay C, then we want to change configure Input Range High = 4mA and Input Range Low = 20 mA in DVC6200 to avoid the reverse status with DCS and valve at site. (DCS is not allowed to changed).
BTW, we can't change Input Range High and Input Range Low sucessful. Could you please advise me? Many thanks.
Model: DVC6200-SISInput: 4-20 mAOutput Signal: Single direct Relay CPower supply; I I to 30 VDCAir supply: 0-10 barMagnet Assemblies; SSTEM #100 ASSEMBLY (f00m]n / 4 INCH)Connections:- Supply and output pressure gauges- Supply Pressure: l/4" NPT intemal and integral pad formounting 67CFR r€gulator- Output Pressure: l/4" FNPT- Electrical connection: l/2" FNPTElectrical Housing (Stainless steel housing): IP66,Intrinsically Safe, Explosion-proof, Division 2, Dust Ignition-proof
In reply to Riyaz Ali:
In reply to Truyen:
This is the official online community site of the Emerson Global Users Exchange, a forum for the free exchange of non-proprietary information among the global user community of all Emerson Automation Solution's products and services. Our goal is to improve the efficiency and use of automation systems and solutions employed at members’ facilities by sharing our knowledge, experiences, and application information.
User Groups |
World Areas |
Community Guidelines |
Legal Information |
Contact Community Manager
Website translation provided by
© 2015-2019 Emerson Global Users Exchange. All rights reserved.