I am studying the feasibility of converting a manual valve to a motor operated one.
Any suggestions please, from practical experience.
from the valve perspective you should also consider,
- valve Maximum Admissible Stem Torque/Trust (MAST)
- stroking speed design limitation
- valve packing original design (how often now will you operate the valve?)
- valve Top Mounting, maybe you will need for an additional std flange
Anyhow it really depends from the kind of valve you have installed and the related expected service.
Feel free to contact me to discuss further.
Paolo Tomaini | Sales & Development Manager | Power & Steam Europe | Final Control
Emerson Automation Solutions | via Castellanza 47 | Rescaldina (MI) | Italy
T +39 0331 575 270 | Paolo.Tomaini@emerson.com | http://www.emerson.com
In reply to Ron:
In reply to Paolo Tomaini:
This is the official online community site of the Emerson Global Users Exchange, a forum for the free exchange of non-proprietary information among the global user community of all Emerson Automation Solution's products and services. Our goal is to improve the efficiency and use of automation systems and solutions employed at members’ facilities by sharing our knowledge, experiences, and application information.
User Groups |
World Areas |
Community Guidelines |
Legal Information |
Contact Community Manager
Website translation provided by
© 2015 Emerson Global Users Exchange. All rights reserved.