Direct-operated regulators are the first choice unless the flow or accuracy requirements cannot be met.
Accuracy - Direct-operated regulators are much less accurate than pilot-operated regulators. Some direct-op products designed for low pressure settings (less than 1 psi) achieve high accuracy by taking advantage of boost. However, in general direct-operated regulators require 20%-40% offset from setpoint whereas pilot-operated regulators require 1%-5%.
Capacity - Pilot-operated regulators are available in larger sizes and therefore higher capacity. Because of their superior accuracy, essentially all of a pilot-operated regulator’s flow capability is usable whereas direct-operated regulator’s useful flow capacity is limited due to excessive droop.
Response Time - Direct-operated regulators have the fastest speed-of-response because changes in outlet pressure move the diaphragm which is tied directly to valve plug travel. Pilot-operated regulators go through the same chain of events but then loading pressure must change prior to repositioning the main valve. Loading-style pilot-ops are slightly faster than unloading-style because the main valve diaphragm senses outlet pressure giving the main valve a head start for outlet pressure changes.
Minimum Differential Requirement - Direct-ops don’t have a required minimum differential. They can continue controlling regardless of pressure differential whereas pilot-operated regulators require a pressure differential between their inlet and outlet in order to open the main valve. Unloading-style pilot-ops have small diaphragms which require higher differential pressures to fully open the main valve.
Cost/Maintenance - Direct-operated regulators are the least complex and most compact of the regulator styles making them the least expensive and easiest to maintain. Unloading-style pilot-ops are the next least costly because of their simplistic main valve design which merges the diaphragm and valve plug into one component, the boot.
This is the official online community site of the Emerson Global Users Exchange, a forum for the free exchange of non-proprietary information among the global user community of all Emerson Automation Solution's products and services. Our goal is to improve the efficiency and use of automation systems and solutions employed at members’ facilities by sharing our knowledge, experiences, and application information.
User Groups |
World Areas |
Community Guidelines |
Legal Information |
Contact Community Manager
Website translation provided by
© 2015-2019 Emerson Global Users Exchange. All rights reserved.